The diagrams on this page illustrate connecting multiple lights in 3 way and 4 way switch circuits. Check below for more details about these circuits and some troubleshooting tips.
At the lights the hot source is spliced to the black wire at each fixture box, at the last fixture it is spliced to the black wire running to the common on SW1. The neutral from the source is connected to each light fixture with a pigtail and run on to the next light.
In this circuit, two fixtures are shown but more can be added by duplicating the wiring arrangement between the lights for each one added. Here the source is at SW1 and 3-wire cable runs from there to L1. Two, 2-wire cables run between the fixtures, and 3-wire cable runs from the last one to SW2.
The traveler terminals will always be connected from switch to switch. Travelers never connect to a device load or to a source wire. It doesn’t matter which traveler terminal is used for which traveler wire, reversing them should make no difference.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.