Here a receptacle outlet is controlled with a single-pole switch. This is commonly used to turn a table lamp on and off when entering a room. In this diagram, 2-conductor cable runs between SW1 and the outlet. The source is at SW1 and the hot wire is connected to the bottom terminal there. The top terminal is connected to the black cable wire running to the hot terminal on the receptacle and the source neutral is spliced with the white cable wire which runs on to the neutral on the receptacle.
Three-way switches allow for controlling a light fixture from two separate locations, these are usually used at the top and bottom of a flight of stairs or at two different entrances to a room. On this page are several wiring diagrams that can be used to map 3 way lighting circuits depending on the location of the source with relation to the lights.
With this wiring, both the black and white wires are used to carry 120 volts each and the white wire is wrapped with electrical tape to label it hot. This circuit doesn’t make use of a neutral wire and the ground wire is connected to the ground terminal on the device. The slots are configured to accept only plugs from compatible appliances.
Check to be sure the traveler wires only connect between the traveler terminals on the switches. Also be sure the neutral from the source is connected to the neutral terminal at the light. A neutral wire will not be used with these switches, although some smart switches may make use of a neutral wire to operate the device.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.