In this arrangement two 3-way dimmers are used to allow for lowering the lights from both locations. Here the common on the first dimmer connects to the hot source and the common on the second connects to the hot on the light. As with all these types of circuits the traveler wires run between the switches and connect the traveler terminals.
This is another option for wiring a combo device where two sources are used. In this arrangement the connecting tab between the hot terminals on the device is broken off to separate the two. The switch controls a light and the receptacle half of the combo device is always hot.
The top terminal is connected to the black cable wire, and the source neutral is spliced to the white wire which continues on to one of the neutral terminals on the receptacle, it doesn’t matter which, only one connection is needed with the neutral wire.
Here two switches are wired in the same box to control two separate lights. The source is at the switch box and a 2-conductor cable is run to each light. One source is spliced to each switch with a pigtail to power the two lights.
Here two 3 way switches control a wall receptacle that may be used to control a lamp from two entrances to a room. This circuit is wired the same way as the 3 way lights at this link.
A 3-wire cable runs from L1 to L2, 2-wire cable runs from there to the first switch, and 3-wire cable runs between SW1 and SW2. The source hot is spliced to the black wire running between the lights and at the last light, it is spliced to the black wire running through to the common on SW1. The white wire is marked black and spliced to the black wire running to the common on SW2.
In this circuit the source hot is at the common on the 3 way switch and 3-wire cable runs from there to the dimmer. The traveler wires run between the 2 switches and 2-wire cable runs from the dimmer to the light. The neutral from the source is spliced at each box to run through to the neutral terminal on the light fixture. The common on the dimmer is connected to the hot terminal on the light fixture.
The diagrams on this page illustrate connecting multiple lights in 3 way and 4 way switch circuits. Check below for more details about these circuits and some troubleshooting tips.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.