This receptacle can typically be found in living room and bedroom wall outlets. One of these may be controlled with a switch and/or wired to other receptacles in the circuit. For a 15 amp receptacle like this, 14/2 cable with ground should be used to feed the circuit.
In this updated diagram 3-conductor cable runs between the receptacle and switch, and the red cable wire is used to carry the hot source to the bottom terminal on the switch. The neutral from the source is passed through to the switch box using the white wire and in this diagram the white wire is capped with a wire nut.
The traveler wires are run using the other 2-wire cable between the lights and continue on to the traveler terminals on SW2. They don’t connect to the fixtures at all.
At the lights the hot source is spliced to the black wire at each fixture box, at the last fixture it is spliced to the black wire running to the common on SW1. The neutral from the source is connected to each light fixture with a pigtail and run on to the next light.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.