A 3-wire cable runs from L1 to L2, 2-wire cable runs from there to the first switch, and 3-wire cable runs between SW1 and SW2. The source hot is spliced to the black wire running between the lights and at the last light, it is spliced to the black wire running through to the common on SW1. The white wire is marked black and spliced to the black wire running to the common on SW2.
Here two switches are wired in the same box to control two separate lights. The source is at the switch box and a 2-conductor cable is run to each light. One source is spliced to each switch with a pigtail to power the two lights.
In a kitchen where only one outlet box is available and both a switch for a garbage disposal and a gfci receptacle are needed, a a switch/gfci combo can be used as in the diagram at this link.
The following 3 diagrams show the wiring for a specially made dimmer that can be used in these circuits in place of either of the the 3 way switches, or both. This arrangement allows for lowering the lights in a 3 way circuit. After the dimmer level has been set the other switch will turn the lights off and on at that level. This device can be used in place of any of the 3 way switches in these circuits, as well as to dim the lights in a 4 way circuit.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.