Here two 3 way switches control a wall receptacle that may be used to control a lamp from two entrances to a room. This circuit is wired the same way as the 3 way lights at this link.
There are two sets of terminals on a ground fault circuit interrupter (gfci) receptacle: the line terminals and the load terminals. The source from the circuit should be connected to the line terminals and any standard duplex outlet or other device connected to the load terminals will be protected by this gfci.
Here the source is in the middle of the circuit. The dimmer switch is in this box where the hot is connect to the common wire. The common on SW1 is run to the light fixture hot terminal using the white cable wire to the dimmer box where it is spliced with the black cable wire going to the light. The white wire is wrapped with black tape to mark it as hot. The traveler wires are connected in the same way as the above diagrams. The neutral runs directly from the dimmer box to the light fixture.
In this circuit a split receptacle is controlled by two separate switches. With this arrangement two lamps can be plugged into the same receptacle and each can be controlled separately from two different locations.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.