Here two 3 way switches control a wall receptacle that may be used to control a lamp from two entrances to a room. This circuit is wired the same way as the 3 way lights at this link.
When replacing an ungrounded, polarized receptacle use this type and not the grounded type above, unless it is grounded by a jumper wire to a metal outlet box that is tied to the house service panel ground through a continuos metal conduit.
Two-wire cable runs from the switch output to the hot on the light fixture. The source neutral wire is spliced to the neutral on the receptacle half of the combo device and to the white cable wire. At the light it connects to the neutral terminal.
In order for a 4 way circuit to work, the 3 way switches must be wired properly at the the beginning and end of the path. So be sure that the common terminal on one of the 3 ways is wired to the hot source, and the common on the second 3 way is wired to the the hot terminal on the lights.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.