A 30 amp circuit was once the norm for large, high voltage appliances like kitchen ranges. This type of receptacle provides 240 volts and 30 amps of current. The smallest cable allowed for used with a 30-amp circuit is 10 gauge, but 8 gauge may also be found. A 3-conductor cable is needed to carry a total of 240 volts and a neutral return. The circuit is wired to a dedicated 30 amp circuit breaker.
Here two switches are wired in the same box to control two separate lights. The source is at the switch box and a 2-conductor cable is run to each light. One source is spliced to each switch with a pigtail to power the two lights.
This diagram illustrates wiring for a 4 way circuit with the electrical source at the light fixture and the switches coming after. Two-wire cable is run from the light to SW1 and 3-wire cable runs between all the switches. The hot source is spliced through to the common terminal on SW2 and the hot terminal on the light fixture is connected to the common on SW1. The travelers run from SW1 to T1 on the 4 way and from T2 to the travelers on SW2. Note that the white wire is wrapped with black electrical tape when it is used for hot in these circuits.
This is the wiring for a dimmer in a 4 way circuit. To make this circuit work, a 3 way dimmer is used in place of one or both of the standard 3 way switches. A dimmer can be added in this way to any of the circuits on this page. A 3 way dimmer has 4 wires: one common, two travelers and a ground.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.