To wire more than one GFCI receptacle in the same circuit, connect the source to the line terminals on each device using a pigtail splice. The load terminals are not used for this circuit. See more GFCI wiring diagrams at this link.
Also be sure the neutral from the source is connected to the neutral terminal at the light. A neutral wire will not be connected to the switches in these circuits, although some smart switches may make use of a neutral wire to operate the device.
In this diagram the source is at SW1 and the hot is connected to the common terminal there. Three-wire cable runs between the switches and 2-wire cable runs from the dimmer to the light fixture. The travelers from SW1 run to T1 on the 4 way switch and from T2 to the traveler wires on the dimmer. The dimmer common wire is spliced to the hot terminal on the light.
This diagram illustrates wiring for a 4 way circuit with the electrical source at the light fixture and the switches coming after. Two-wire cable is run from the light to SW1 and 3-wire cable runs between all the switches. The hot source is spliced through to the common terminal on SW2 and the hot terminal on the light fixture is connected to the common on SW1. The travelers run from SW1 to T1 on the 4 way and from T2 to the travelers on SW2. Note that the white wire is wrapped with black electrical tape when it is used for hot in these circuits.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.