The 4 way comes right after the light fixture, but before the second 3 way switch, making it fall between the two 3 ways as needed. It could also be installed on the other side of the light and the effect would be the same.
There are two sets of terminals on a ground fault circuit interrupter (gfci) receptacle: the line terminals and the load terminals. The source from the circuit should be connected to the line terminals and any standard duplex outlet or other device connected to the load terminals will be protected by this gfci.
If your switches stop working they may be worn out or the screws may have come loose. If you’ve wired a new switch correctly and the circuit still doesn’t work, the switch may be defective. Check that all connections are tight. Check the switch, remove it from the circuit and test for failure with a continuity tester or multimeter set on the Ohms setting.
If the switch is good and things still don’t work, check the wiring to be sure the hot source is connected to a common terminal and the light fixture hot is connected to a common terminal. Likewise, be sure the traveler terminals are connected between switches only and not to any hot wires or the load.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.