This represents a change in the NEC code that requires a neutral wire in most new switch boxes. If you are running a new circuit check the electrical code to understand this and any other updates to the required procedure.
This receptacle can typically be found in living room and bedroom wall outlets. One of these may be controlled with a switch and/or wired to other receptacles in the circuit. For a 15 amp receptacle like this, 14/2 cable with ground should be used to feed the circuit.
This is the oldest version of a wall receptacle that you will find. It lacks a grounding contact and the plug slots are both the same size. These devices did not make use of a ground wire and both plug slots were treated the same. The wires used with these receptacles were usually both black.
In this updated diagram 3-wire cable runs between the receptacle and SW2 to allow for splicing the neutral source through to the second switch box. Here the white is not used for hot but instead the extra, red wire serves that purpose for the second switch.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.