A 4 way switch must be wired between two 3 ways as shown in the diagrams on this page. A 4 way has five connections: one ground, and 4 circuit terminals divided into two matching pairs. Each pair of terminals should be wired to the traveler wires from one of the 3 way switches. The travelers can be wired to either terminal in a pair, but don’t mix up the pairs or the circuit won’t work properly.
At SW1 the white wire is wrapped with black tape and run through to the common on SW2 using the white wire at each switch. At the lights the white wire from SW2 is spliced to the hot terminal on each fixture. The black and red wires running between the switches serve as the travelers for the circuit. At the 4 way the travelers from SW1 connect to T1 and T2 connect to the travelers for SW2.
In a kitchen where only one outlet box is available and both a switch for a garbage disposal and a gfci receptacle are needed, a a switch/gfci combo can be used as in the diagram at this link.
At the beginning of the circuit the hot source is connected to the common terminal on SW1. The neutral is spliced to the white cable wire and then spliced to the neutral terminal at L1, along with the white 2-cable wire running to L2 where it connects to the neutral terminal.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.