In this circuit the source hot is at the common on the 3 way switch and 3-wire cable runs from there to the dimmer. The traveler wires run between the 2 switches and 2-wire cable runs from the dimmer to the light. The neutral from the source is spliced at each box to run through to the neutral terminal on the light fixture. The common on the dimmer is connected to the hot terminal on the light fixture.
This is an updated version of the first arrangement. Because the electrical code as of the 2011 NEC update requires a neutral wire in most new switch boxes, a 3-wire cable runs between the light and switch. The red and black are used for hot and the white neutral wire at the switch box allows for powering a remote controlled switch.
This is the standard 15 amp 120 volt wall receptacle outlet wiring diagram. This is a polarized device. The long slot on the left is the neutral contact and the short slot is the hot contact. A grounded contact at the bottom, center is crescent shaped. Don’t use this receptacle when no ground wire is available.
The traveler terminals will always be connected from switch to switch. Travelers never connect to a device load or to a source wire. It doesn’t matter which traveler terminal is used for which traveler wire, reversing them should make no difference.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.