This drawing shows the wiring for multiple lights in a 4 way circuit with the source and fixtures coming before the switches. More lights can be added to this circuit by duplicating the wiring shown here for each additional fixture. Here 3-wire cable runs between L1 and L2, 2-wire cable runs from the last fixture to SW1, and 3-wires runs between SW1 and SW2.
A combo switch/receptacle is handy when you need both, but you only have one outlet box available. Like the split receptacles above these devices makes use of a removable connector between the two, hot terminals to divide the device when needed. When intact and wired to one hot source wire, the combo device can be used to turn a light off and on, while the receptacle will be constantly hot.
In this circuit, two fixtures are shown but more can be added by duplicating the wiring arrangement between the lights for each one added. Here the source is at SW1 and 3-wire cable runs from there to L1. Two, 2-wire cables run between the fixtures, and 3-wire cable runs from the last one to SW2.
This is the standard 15 amp 120 volt wall receptacle outlet wiring diagram. This is a polarized device. The long slot on the left is the neutral contact and the short slot is the hot contact. A grounded contact at the bottom, center is crescent shaped. Don’t use this receptacle when no ground wire is available.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.