Here again, the connecting tab between the receptacle terminals is broken off and the neutral tab remains intact. The source is at SW1 and 3-conductor cable runs from there to the receptacle, 2-conductor cable runs from the receptacle to SW2. The source hot wire is spliced to the bottom terminal on SW1 and to the red cable running to the receptacle.
This diagram shows the wiring to control a receptacle outlet with two 3 way switches. The source is at SW1 and 3-wire cable runs between all the devices. The hot wire from the source connects to the common terminal on SW1. The common on SW2 is connected to the hot terminal on the receptacle. The traveler wires are spliced in the receptacle box to run to the traveler terminals on each switch. The white cable wire is used as a traveler to SW2 and marked hot with black tape.
The common wire is usually black and the travelers red, in any case, the traveler wires will usually be the same color to distinguish them from the common. The stranded wires on the dimmer are spliced to the cable wires from the circuit.
This wiring shows the light fixture and the electrical source between the switches. Three-wire cable runs throughout and the hot source is splice to the common on SW1. The common on SW2 is spliced through to the hot on the light fixture. The travelers from SW1 are spliced at the fixture outlet box to run to the 4 way switch.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.