This page contains wiring diagrams for most household receptacle you will encounter including grounded and ungrounded duplex outlets, ground fault circuit interrupters (GFCI) as well as 20amp, 30amp and 50amp receptacles for 120 volt and 240 volt circuits.
This receptacle can typically be found in living room and bedroom wall outlets. One of these may be controlled with a switch and/or wired to other receptacles in the circuit. For a 15 amp receptacle like this, 14/2 cable with ground should be used to feed the circuit.
The wiring diagrams on this page make use of 4 way switches, between two 3 way switches, to control lights from three or more locations. A 4-way dimmer diagram is included as well as an arrangement to control the lights from four different points. Check here for 4 way switch troubleshooting and help with 3 ways switches here. For circuits that control lights from two locations only, check the wiring diagrams at this link.
Here the source is at the receptacle and 2-conductor cable runs from there to SW1. The hot source is spliced to a pigtail that connect to the bottom, always-hot, half on the receptacle and to the white cable wire which continues on to the bottom terminal on SW1. The black cable wire is connected to the top terminal on the split receptacle and runs to the top terminal on SW1. The circuit neutral wire is connected to one of the neutral terminals on the receptacle, it doesn’t run to the switch.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.