Here two 3 way switches control a wall receptacle that may be used to control a lamp from two entrances to a room. This circuit is wired the same way as the 3 way lights at this link.
This outlet is commonly used for a heavy load such as a large air conditioner. The outlet should be wired to a dedicated 20-amp/240-volt circuit breaker in the service panel using 12|2 awg cable.
Here a receptacle outlet is controlled with a single-pole switch. This is commonly used to turn a table lamp on and off when entering a room. In this diagram, 2-conductor cable runs between SW1 and the outlet. The source is at SW1 and the hot wire is connected to the bottom terminal there. The top terminal is connected to the black cable wire running to the hot terminal on the receptacle and the source neutral is spliced with the white cable wire which runs on to the neutral on the receptacle.
This diagram illustrates another multiple light circuit controlled by 3 way switches. Here the source and the fixtures come before the switches. As with the other diagrams on this page, more lights can be added by duplicating the arrangement between the fixtures.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.