In this updated diagram 3-conductor cable runs between the receptacle and switch, and the red cable wire is used to carry the hot source to the bottom terminal on the switch. The neutral from the source is passed through to the switch box using the white wire and in this diagram the white wire is capped with a wire nut.
The traveler wires are run using the other 2-wire cable between the lights and continue on to the traveler terminals on SW2. They don’t connect to the fixtures at all.
At SW1 the white wire is wrapped with black tape and run through to the common on SW2 using the white wire at each switch. At the lights the white wire from SW2 is spliced to the hot terminal on each fixture. The black and red wires running between the switches serve as the travelers for the circuit. At the 4 way the travelers from SW1 connect to T1 and T2 connect to the travelers for SW2.
The traveler terminals will always be connected from switch to switch. Travelers never connect to a device load or to a source wire. It doesn’t matter which traveler terminal is used for which traveler wire, reversing them should make no difference.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.