When replacing an ungrounded, polarized receptacle use this type and not the grounded type above, unless it is grounded by a jumper wire to a metal outlet box that is tied to the house service panel ground through a continuos metal conduit.
Here again, the connecting tab between the receptacle terminals is broken off and the neutral tab remains intact. The source is at SW1 and 3-conductor cable runs from there to the receptacle, 2-conductor cable runs from the receptacle to SW2. The source hot wire is spliced to the bottom terminal on SW1 and to the red cable running to the receptacle.
The diagrams on this page illustrate connecting multiple lights in 3 way and 4 way switch circuits. Check below for more details about these circuits and some troubleshooting tips.
The wiring diagrams on this page make use of 4 way switches, between two 3 way switches, to control lights from three or more locations. A 4-way dimmer diagram is included as well as an arrangement to control the lights from four different points. Check here for 4 way switch troubleshooting and help with 3 ways switches here. For circuits that control lights from two locations only, check the wiring diagrams at this link.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.