This represents a change in the NEC code that requires a neutral wire in most new switch boxes. If you are running a new circuit check the electrical code to understand this and any other updates to the required procedure.
If the switch is good and things still don’t work, check the wiring to be sure the hot source is connected to a common terminal and the light fixture hot is connected to a common terminal. Likewise, be sure the traveler terminals are connected between switches only and not to any hot wires or the load.
The wiring diagrams on this page make use of 4 way switches, between two 3 way switches, to control lights from three or more locations. A 4-way dimmer diagram is included as well as an arrangement to control the lights from four different points. Check here for 4 way switch troubleshooting and help with 3 ways switches here. For circuits that control lights from two locations only, check the wiring diagrams at this link.
This page contains wiring diagrams for most household receptacle you will encounter including grounded and ungrounded duplex outlets, ground fault circuit interrupters (GFCI) as well as 20amp, 30amp and 50amp receptacles for 120 volt and 240 volt circuits.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.