In this updated diagram 3-conductor cable runs between the receptacle and switch, and the red cable wire is used to carry the hot source to the bottom terminal on the switch. The neutral from the source is passed through to the switch box using the white wire and in this diagram the white wire is capped with a wire nut.
In order for a 4 way circuit to work, the 3 way switches must be wired properly at the the beginning and end of the path. So be sure that the common terminal on one of the 3 ways is wired to the hot source, and the common on the second 3 way is wired to the the hot terminal on the lights.
The neutral wire provides a return path for the circuit and the ground wire provides extra protection from electrocution not found on older 30 amp, 240 volt appliance hookups.
Here a receptacle outlet is controlled with a single-pole switch. This is commonly used to turn a table lamp on and off when entering a room. In this diagram, 2-conductor cable runs between SW1 and the outlet. The source is at SW1 and the hot wire is connected to the bottom terminal there. The top terminal is connected to the black cable wire running to the hot terminal on the receptacle and the source neutral is spliced with the white cable wire which runs on to the neutral on the receptacle.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.