A 3-wire cable runs from L1 to L2, 2-wire cable runs from there to the first switch, and 3-wire cable runs between SW1 and SW2. The source hot is spliced to the black wire running between the lights and at the last light, it is spliced to the black wire running through to the common on SW1. The white wire is marked black and spliced to the black wire running to the common on SW2.
This is another option for wiring a combo device where two sources are used. In this arrangement the connecting tab between the hot terminals on the device is broken off to separate the two. The switch controls a light and the receptacle half of the combo device is always hot.
Three-way switches allow for controlling a light fixture from two separate locations, these are usually used at the top and bottom of a flight of stairs or at two different entrances to a room. On this page are several wiring diagrams that can be used to map 3 way lighting circuits depending on the location of the source with relation to the lights.
This arrangement makes it possible to power the heating elements in the appliance using the two 120 volts combined and one 120 volt wire to power timers and lights. This circuit is still used for clothes dryers but not for most new installations of kitchen ranges, for that a 50 amp circuit (pictured below) is now used.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.