Here a receptacle is added to the circuit before the first switch. It is not controlled with the switches but is instead always hot. The source hot, neutral and ground are spliced to a 2-wire cable that runs to the new outlet. The 3 way switches and light are then wired in the usual way with the common on SW2 spliced to the source hot and the light hot wired to the common on SW1.
The common wire is usually black and the travelers red, in any case, the traveler wires will usually be the same color to distinguish them from the common. The stranded wires on the dimmer are spliced to the cable wires from the circuit.
To wire more than one GFCI receptacle in the same circuit, connect the source to the line terminals on each device using a pigtail splice. The load terminals are not used for this circuit. See more GFCI wiring diagrams at this link.
At the receptacle the black cable wire from SW1 is connected to one of the hot terminals and the red wire is spliced to the white wire on the 2-conductor cable running to SW2. The white wire is wrapped with electrical tape to mark it as hot. The black wire is connected to the second hot terminal on the receptacle and to the top terminal on SW2 at the other end.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.