The top terminal is connected to the black cable wire, and the source neutral is spliced to the white wire which continues on to one of the neutral terminals on the receptacle, it doesn’t matter which, only one connection is needed with the neutral wire.
Included is a diagram for a 3 way dimmer and an arrangement to control a receptacle from two locations. For more information about these circuits and troubleshooting tips check below.
In this updated diagram 3-wire cable runs between the receptacle and SW2 to allow for splicing the neutral source through to the second switch box. Here the white is not used for hot but instead the extra, red wire serves that purpose for the second switch.
If the switch is good and things still don’t work, check the wiring to be sure the hot source is connected to a common terminal and the light fixture hot is connected to a common terminal. Likewise, be sure the traveler terminals are connected between switches only and not to any hot wires or the load.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.