Three-way switches allow for controlling a light fixture from two separate locations, these are usually used at the top and bottom of a flight of stairs or at two different entrances to a room. On this page are several wiring diagrams that can be used to map 3 way lighting circuits depending on the location of the source with relation to the lights.
To wire this circuit, 2-conductor cable runs from the dimmer to the light. The source is at the dimmer and the hot wire is spliced to one hot wire on the device. The other wire from the dimmer is spliced to the black cable wire which runs on to the hot terminal on the light. The source neutral wire is spliced to the white cable wire which continues on to the neutral terminal on the light.
This receptacle can typically be found in living room and bedroom wall outlets. One of these may be controlled with a switch and/or wired to other receptacles in the circuit. For a 15 amp receptacle like this, 14/2 cable with ground should be used to feed the circuit.
This diagram is the same as the one above but the dimmer comes first in the circuit. This arrangement is provided for easy reference when dealing with a circuit wired like this.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.