In this arrangement the source for the circuit is at the light fixture. 3-wire cable runs from the switches on each side, to the light. The hot source is spliced to the common terminal on SW2 and the hot terminal on the light fixture connects to the common terminal on SW1. The traveler wires are spliced at the fixture box and run to the traveler terminals on both switches.
Two-wire cable runs from the switch output to the hot on the light fixture. The source neutral wire is spliced to the neutral on the receptacle half of the combo device and to the white cable wire. At the light it connects to the neutral terminal.
There are two sets of terminals on a ground fault circuit interrupter (gfci) receptacle: the line terminals and the load terminals. The source from the circuit should be connected to the line terminals and any standard duplex outlet or other device connected to the load terminals will be protected by this gfci.
Back at the lights the source neutral is connected to the neutral terminal on L1 and spliced with the white wire running between the fixtures. At each light it’s connected to the neutral terminal. At SW1 the red and white wires from the 3-wire cable running between switches function as the travelers with the white marked for hot using black tape or paint.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.