In this circuit, two fixtures are shown but more can be added by duplicating the wiring arrangement between the lights for each one added. Here the source is at SW1 and 3-wire cable runs from there to L1. Two, 2-wire cables run between the fixtures, and 3-wire cable runs from the last one to SW2.
Here the source is in the middle of the circuit. The dimmer switch is in this box where the hot is connect to the common wire. The common on SW1 is run to the light fixture hot terminal using the white cable wire to the dimmer box where it is spliced with the black cable wire going to the light. The white wire is wrapped with black tape to mark it as hot. The traveler wires are connected in the same way as the above diagrams. The neutral runs directly from the dimmer box to the light fixture.
To wire this circuit, 2-conductor cable runs from the dimmer to the light. The source is at the dimmer and the hot wire is spliced to one hot wire on the device. The other wire from the dimmer is spliced to the black cable wire which runs on to the hot terminal on the light. The source neutral wire is spliced to the white cable wire which continues on to the neutral terminal on the light.
This is an older version of the receptacle in the first diagram. The slots are different sizes to accept polarized plugs, but it lacks a grounding slot. This device does not make use of a ground wire. There is no protection against electrocution as provide by the grounded receptacle.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.