To wire this circuit, 2-conductor cable runs from the dimmer to the light. The source is at the dimmer and the hot wire is spliced to one hot wire on the device. The other wire from the dimmer is spliced to the black cable wire which runs on to the hot terminal on the light. The source neutral wire is spliced to the white cable wire which continues on to the neutral terminal on the light.
At SW1 the white wire is wrapped with black tape and run through to the common on SW2 using the white wire at each switch. At the lights the white wire from SW2 is spliced to the hot terminal on each fixture. The black and red wires running between the switches serve as the travelers for the circuit. At the 4 way the travelers from SW1 connect to T1 and T2 connect to the travelers for SW2.
Three-way switches allow for controlling a light fixture from two separate locations, these are usually used at the top and bottom of a flight of stairs or at two different entrances to a room. On this page are several wiring diagrams that can be used to map 3 way lighting circuits depending on the location of the source with relation to the lights.
If the switch is good and things still don’t work, check the wiring to be sure the hot source is connected to a common terminal and the light fixture hot is connected to a common terminal. Likewise, be sure the traveler terminals are connected between switches only and not to any hot wires or the load.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.