This diagram illustrates the wiring for a split receptacle with the top half controlled by SW1 and the bottom half always hot. The receptacle is split by breaking the connecting tab between the two, brass colored terminals. The tab between the neutral, silver terminals should remain intact.
Two-wire cable runs from the switch output to the hot on the light fixture. The source neutral wire is spliced to the neutral on the receptacle half of the combo device and to the white cable wire. At the light it connects to the neutral terminal.
If your switches stop working they may be worn out or the screws may have come loose. If you’ve wired a new switch correctly and the circuit still doesn’t work, the switch may be defective. Check that all connections are tight. Check the switch, remove it from the circuit and test for failure with a continuity tester or multimeter set on the Ohms setting.
The diagrams on this page illustrate connecting multiple lights in 3 way and 4 way switch circuits. Check below for more details about these circuits and some troubleshooting tips.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.