This page contains wiring diagrams for most household receptacle you will encounter including grounded and ungrounded duplex outlets, ground fault circuit interrupters (GFCI) as well as 20amp, 30amp and 50amp receptacles for 120 volt and 240 volt circuits.
If the switch is good and things still don’t work, check the wiring to be sure the hot source is connected to a common terminal and the light fixture hot is connected to a common terminal. Likewise, be sure the traveler terminals are connected between switches only and not to any hot wires or the load.
Here a receptacle is added to the circuit before the first switch. It is not controlled with the switches but is instead always hot. The source hot, neutral and ground are spliced to a 2-wire cable that runs to the new outlet. The 3 way switches and light are then wired in the usual way with the common on SW2 spliced to the source hot and the light hot wired to the common on SW1.
The common terminals will always be connected to a hot wire, either from the source or on the light fixture. These connections can be reversed if it’s more convenient, as long as one of the 3 way common terminals connects to the hot source and the other one connects to the hot on the load, these circuits will work properly.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.