A 3-wire cable runs from L1 to L2, 2-wire cable runs from there to the first switch, and 3-wire cable runs between SW1 and SW2. The source hot is spliced to the black wire running between the lights and at the last light, it is spliced to the black wire running through to the common on SW1. The white wire is marked black and spliced to the black wire running to the common on SW2.
When the electrical source originates at a light fixture and it’s controlled from a remote location, a switch loop is used. The circuit pictured here is wired with 2-conductor cable running from the light to the switch location. The white cable wire in this switch loop is wrapped with black tape and connected to the bottom terminal on SW1 and the hot source at the light. The black wire is connected to the top terminal on SW1 and the hot terminal on the light fixture. The neutral from the source is connected directly to the neutral terminal on the light.
This diagram illustrates wiring for a 4 way circuit with the electrical source at the light fixture and the switches coming after. Two-wire cable is run from the light to SW1 and 3-wire cable runs between all the switches. The hot source is spliced through to the common terminal on SW2 and the hot terminal on the light fixture is connected to the common on SW1. The travelers run from SW1 to T1 on the 4 way and from T2 to the travelers on SW2. Note that the white wire is wrapped with black electrical tape when it is used for hot in these circuits.
Here two 3 way switches control a wall receptacle that may be used to control a lamp from two entrances to a room. This circuit is wired the same way as the 3 way lights at this link.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.