At the receptacle the black cable wire from SW1 is connected to one of the hot terminals and the red wire is spliced to the white wire on the 2-conductor cable running to SW2. The white wire is wrapped with electrical tape to mark it as hot. The black wire is connected to the second hot terminal on the receptacle and to the top terminal on SW2 at the other end.
With this configuration any wire in the circuit may be hot at all times and there’s no protection against electrocution. When replacing an ungrounded device in an older circuit like this, use the polarized one above and not the grounded receptacle at the top unless it is grounded to a metal outlet box that is itself grounded to the house electrical system through a continuos metal conduit.
This diagram illustrates the wiring for a split receptacle with the top half controlled by SW1 and the bottom half always hot. The receptacle is split by breaking the connecting tab between the two, brass colored terminals. The tab between the neutral, silver terminals should remain intact.
In this basic 4 way light circuit the source is at the first switch and the hot connects to the common on that switch. Three-wire cable runs between all the switches and the traveler wires are connected between the two 3-ways and the 4-way. Two-wire cable runs from the last switch to the light fixture and the common on that switch connects to the hot terminal on the light.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.