Included is a diagram for a 3 way dimmer and an arrangement to control a receptacle from two locations. For more information about these circuits and troubleshooting tips check below.
Here two 4 way and two 3 way switches are used to control lights from four different locations. The source is at SW1 and the hot wire is connected to the common terminal. Three-wire cable runs between all switches and 2-wire cable runs from the last switch to the light fixture. The light hot connects to the common terminal on SW2.
A combo switch/receptacle is handy when you need both, but you only have one outlet box available. Like the split receptacles above these devices makes use of a removable connector between the two, hot terminals to divide the device when needed. When intact and wired to one hot source wire, the combo device can be used to turn a light off and on, while the receptacle will be constantly hot.
This diagram illustrates wiring for one switch to control multiple lights. The source is at SW1 and 2-conductor cable runs from there to the fixtures. The hot and neutral terminals on each fixture are spliced with a pigtail to the circuit wires which then continue on to the next light. This is the simplest arrangement for more than one light on a single switch.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.