Here two 3 way switches control a wall receptacle that may be used to control a lamp from two entrances to a room. This circuit is wired the same way as the 3 way lights at this link.
If your switches stop working they may be worn out or the screws may have come loose. If you’ve wired a new switch correctly and the circuit still doesn’t work, the switch may be defective. Check that all connections are tight. Check the switch, remove it from the circuit and test for failure with a continuity tester or multimeter set on the Ohms setting.
Here a receptacle outlet is controlled with a single-pole switch. This is commonly used to turn a table lamp on and off when entering a room. In this diagram, 2-conductor cable runs between SW1 and the outlet. The source is at SW1 and the hot wire is connected to the bottom terminal there. The top terminal is connected to the black cable wire running to the hot terminal on the receptacle and the source neutral is spliced with the white cable wire which runs on to the neutral on the receptacle.
This is the wiring for a dimmer in a 4 way circuit. To make this circuit work, a 3 way dimmer is used in place of one or both of the standard 3 way switches. A dimmer can be added in this way to any of the circuits on this page. A 3 way dimmer has 4 wires: one common, two travelers and a ground.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.