Here two 3 way switches control a wall receptacle that may be used to control a lamp from two entrances to a room. This circuit is wired the same way as the 3 way lights at this link.
This wiring diagram is used for 50 and 60 amp circuits. The receptacle should be wired to a dedicated 50 or 60 amp circuit breaker using 6 awg cable. The 50 amp circuit is required for new installations of some large appliances requiring 240 volts. Two wires carrying 120 volts each can be combined to provide high voltage to heating circuits and one of the 120 volt wires can serve lights or other low voltage circuits in the appliance.
A 3-wire cable runs from L1 to L2, 2-wire cable runs from there to the first switch, and 3-wire cable runs between SW1 and SW2. The source hot is spliced to the black wire running between the lights and at the last light, it is spliced to the black wire running through to the common on SW1. The white wire is marked black and spliced to the black wire running to the common on SW2.
The traveler terminals will always be connected from switch to switch. Travelers never connect to a device load or to a source wire. It doesn’t matter which traveler terminal is used for which traveler wire, reversing them should make no difference.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.