A combo switch/receptacle is handy when you need both, but you only have one outlet box available. Like the split receptacles above these devices makes use of a removable connector between the two, hot terminals to divide the device when needed. When intact and wired to one hot source wire, the combo device can be used to turn a light off and on, while the receptacle will be constantly hot.
This is an updated version of the first arrangement. Because the electrical code as of the 2011 NEC update requires a neutral wire in most new switch boxes, a 3-wire cable runs between the light and switch. The red and black are used for hot and the white neutral wire at the switch box allows for powering a remote controlled switch.
In this arrangement the source for the circuit is at the light fixture. 3-wire cable runs from the switches on each side, to the light. The hot source is spliced to the common terminal on SW2 and the hot terminal on the light fixture connects to the common terminal on SW1. The traveler wires are spliced at the fixture box and run to the traveler terminals on both switches.
The following 3 diagrams show the wiring for a specially made dimmer that can be used in these circuits in place of either of the the 3 way switches, or both. This arrangement allows for lowering the lights in a 3 way circuit. After the dimmer level has been set the other switch will turn the lights off and on at that level. This device can be used in place of any of the 3 way switches in these circuits, as well as to dim the lights in a 4 way circuit.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.