A 30 amp circuit was once the norm for large, high voltage appliances like kitchen ranges. This type of receptacle provides 240 volts and 30 amps of current. The smallest cable allowed for used with a 30-amp circuit is 10 gauge, but 8 gauge may also be found. A 3-conductor cable is needed to carry a total of 240 volts and a neutral return. The circuit is wired to a dedicated 30 amp circuit breaker.
If the switch is good and things still don’t work, check the wiring to be sure the hot source is connected to a common terminal and the light fixture hot is connected to a common terminal. Likewise, be sure the traveler terminals are connected between switches only and not to any hot wires or the load.
In this circuit a split receptacle is controlled by two separate switches. With this arrangement two lamps can be plugged into the same receptacle and each can be controlled separately from two different locations.
The source in this circuit is at the first switch and the light fixture is located between SW1 and SW2. Three-wire cable runs between each switch and the light fixture. The hot source wire is connected to the common terminal on SW1. The common terminal on SW2 is connected to the hot terminal on the light. The traveler wires are spliced at the fixture box to run between the traveler terminals on the switches.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.