Check to be sure the traveler wires only connect between the traveler terminals on the switches. Also be sure the neutral from the source is connected to the neutral terminal at the light. A neutral wire will not be used with these switches, although some smart switches may make use of a neutral wire to operate the device.
At the receptacle the black cable wire from SW1 is connected to one of the hot terminals and the red wire is spliced to the white wire on the 2-conductor cable running to SW2. The white wire is wrapped with electrical tape to mark it as hot. The black wire is connected to the second hot terminal on the receptacle and to the top terminal on SW2 at the other end.
A 4 way switch must be wired between two 3 ways as shown in the diagrams on this page. A 4 way has five connections: one ground, and 4 circuit terminals divided into two matching pairs. Each pair of terminals should be wired to the traveler wires from one of the 3 way switches. The travelers can be wired to either terminal in a pair, but don’t mix up the pairs or the circuit won’t work properly.
This outlet is commonly used for a heavy load such as a large air conditioner. The outlet should be wired to a dedicated 20-amp/240-volt circuit breaker in the service panel using 12|2 awg cable.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.