Back at the lights the source neutral is connected to the neutral terminal on L1 and spliced with the white wire running between the fixtures. At each light it’s connected to the neutral terminal. At SW1 the red and white wires from the 3-wire cable running between switches function as the travelers with the white marked for hot using black tape or paint.
This diagram shows the first wiring option for this device. In this arrangement the connecting tab between the hot terminals remains intact. The source is at the device and the hot is connected directly to one of the hot terminals, it doesn’t matter which one.
A combo switch/receptacle is handy when you need both, but you only have one outlet box available. Like the split receptacles above these devices makes use of a removable connector between the two, hot terminals to divide the device when needed. When intact and wired to one hot source wire, the combo device can be used to turn a light off and on, while the receptacle will be constantly hot.
This page contains wiring diagrams for most household receptacle you will encounter including grounded and ungrounded duplex outlets, ground fault circuit interrupters (GFCI) as well as 20amp, 30amp and 50amp receptacles for 120 volt and 240 volt circuits.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.