If the switch is good and things still don’t work, check the wiring to be sure the hot source is connected to a common terminal and the light fixture hot is connected to a common terminal. Likewise, be sure the traveler terminals are connected between switches only and not to any hot wires or the load.
Included is a diagram for a 3 way dimmer and an arrangement to control a receptacle from two locations. For more information about these circuits and troubleshooting tips check below.
With this configuration any wire in the circuit may be hot at all times and there’s no protection against electrocution. When replacing an ungrounded device in an older circuit like this, use the polarized one above and not the grounded receptacle at the top unless it is grounded to a metal outlet box that is itself grounded to the house electrical system through a continuos metal conduit.
In this diagram the electrical source is at the first switch and the light is located at the end of the circuit. Three-wire cable runs between the switches and 2-wire cable runs to the light. The black and red wires between SW1 and SW2 are connected to the traveler terminals. The hot source is connected to the common terminal on SW1, and the common terminal on SW2 connects to the hot terminal on the light.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.