This diagram is the same as the one above but the dimmer comes first in the circuit. This arrangement is provided for easy reference when dealing with a circuit wired like this.
When the electrical source originates at a light fixture and it’s controlled from a remote location, a switch loop is used. The circuit pictured here is wired with 2-conductor cable running from the light to the switch location. The white cable wire in this switch loop is wrapped with black tape and connected to the bottom terminal on SW1 and the hot source at the light. The black wire is connected to the top terminal on SW1 and the hot terminal on the light fixture. The neutral from the source is connected directly to the neutral terminal on the light.
Back at the lights the source neutral is connected to the neutral terminal on L1 and spliced with the white wire running between the fixtures. At each light it’s connected to the neutral terminal. At SW1 the red and white wires from the 3-wire cable running between switches function as the travelers with the white marked for hot using black tape or paint.
A combo switch/receptacle is handy when you need both, but you only have one outlet box available. Like the split receptacles above these devices makes use of a removable connector between the two, hot terminals to divide the device when needed. When intact and wired to one hot source wire, the combo device can be used to turn a light off and on, while the receptacle will be constantly hot.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.