This diagram illustrates the wiring for a split receptacle with the top half controlled by SW1 and the bottom half always hot. The receptacle is split by breaking the connecting tab between the two, brass colored terminals. The tab between the neutral, silver terminals should remain intact.
Here a receptacle outlet is controlled with a single-pole switch. This is commonly used to turn a table lamp on and off when entering a room. In this diagram, 2-conductor cable runs between SW1 and the outlet. The source is at SW1 and the hot wire is connected to the bottom terminal there. The top terminal is connected to the black cable wire running to the hot terminal on the receptacle and the source neutral is spliced with the white cable wire which runs on to the neutral on the receptacle.
The 4 way comes right after the light fixture, but before the second 3 way switch, making it fall between the two 3 ways as needed. It could also be installed on the other side of the light and the effect would be the same.
Check to be sure the traveler wires only connect between the traveler terminals on the switches. Also be sure the neutral from the source is connected to the neutral terminal at the light. A neutral wire will not be used with these switches, although some smart switches may make use of a neutral wire to operate the device.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.