Here the source is at SW1 and the light fixture comes immediately after. The source neutral is spliced through to the light fixture. At the light the travelers are splice together and run to the 4-way switch. At the 4-way, the hot wire from the common terminal on SW2 is splice through to the hot on the light fixture.
With this wiring, both the black and white wires are used to carry 120 volts each and the white wire is wrapped with electrical tape to label it hot. This circuit doesn’t make use of a neutral wire and the ground wire is connected to the ground terminal on the device. The slots are configured to accept only plugs from compatible appliances.
The wiring diagrams on this page make use of 4 way switches, between two 3 way switches, to control lights from three or more locations. A 4-way dimmer diagram is included as well as an arrangement to control the lights from four different points. Check here for 4 way switch troubleshooting and help with 3 ways switches here. For circuits that control lights from two locations only, check the wiring diagrams at this link.
To wire more than one GFCI receptacle in the same circuit, connect the source to the line terminals on each device using a pigtail splice. The load terminals are not used for this circuit. See more GFCI wiring diagrams at this link.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.