The common terminals will always be connected to a hot wire, either from the source or on the light fixture. These connections can be reversed if it’s more convenient, as long as one of the 3 way common terminals connects to the hot source and the other one connects to the hot on the load, these circuits will work properly.
At the beginning of the circuit the hot source is connected to the common terminal on SW1. The neutral is spliced to the white cable wire and then spliced to the neutral terminal at L1, along with the white 2-cable wire running to L2 where it connects to the neutral terminal.
This receptacle can typically be found in living room and bedroom wall outlets. One of these may be controlled with a switch and/or wired to other receptacles in the circuit. For a 15 amp receptacle like this, 14/2 cable with ground should be used to feed the circuit.
When the electrical source originates at a light fixture and it’s controlled from a remote location, a switch loop is used. The circuit pictured here is wired with 2-conductor cable running from the light to the switch location. The white cable wire in this switch loop is wrapped with black tape and connected to the bottom terminal on SW1 and the hot source at the light. The black wire is connected to the top terminal on SW1 and the hot terminal on the light fixture. The neutral from the source is connected directly to the neutral terminal on the light.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.