This wiring shows the light fixture and the electrical source between the switches. Three-wire cable runs throughout and the hot source is splice to the common on SW1. The common on SW2 is spliced through to the hot on the light fixture. The travelers from SW1 are spliced at the fixture outlet box to run to the 4 way switch.
In order for a 4 way circuit to work, the 3 way switches must be wired properly at the the beginning and end of the path. So be sure that the common terminal on one of the 3 ways is wired to the hot source, and the common on the second 3 way is wired to the the hot terminal on the lights.
Here the source is at SW1 and the light fixture comes immediately after. The source neutral is spliced through to the light fixture. At the light the travelers are splice together and run to the 4-way switch. At the 4-way, the hot wire from the common terminal on SW2 is splice through to the hot on the light fixture.
The 4 way comes right after the light fixture, but before the second 3 way switch, making it fall between the two 3 ways as needed. It could also be installed on the other side of the light and the effect would be the same.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.