This diagram shows the wiring to control a receptacle outlet with two 3 way switches. The source is at SW1 and 3-wire cable runs between all the devices. The hot wire from the source connects to the common terminal on SW1. The common on SW2 is connected to the hot terminal on the receptacle. The traveler wires are spliced in the receptacle box to run to the traveler terminals on each switch. The white cable wire is used as a traveler to SW2 and marked hot with black tape.
The neutral wire provides a return path for the circuit and the ground wire provides extra protection from electrocution not found on older 30 amp, 240 volt appliance hookups.
There are two sets of terminals on a ground fault circuit interrupter (gfci) receptacle: the line terminals and the load terminals. The source from the circuit should be connected to the line terminals and any standard duplex outlet or other device connected to the load terminals will be protected by this gfci.
Here the source is in the middle of the circuit. The dimmer switch is in this box where the hot is connect to the common wire. The common on SW1 is run to the light fixture hot terminal using the white cable wire to the dimmer box where it is spliced with the black cable wire going to the light. The white wire is wrapped with black tape to mark it as hot. The traveler wires are connected in the same way as the above diagrams. The neutral runs directly from the dimmer box to the light fixture.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.