If your switches stop working they may be worn out or the screws may have come loose. If you’ve wired a new switch correctly and the circuit still doesn’t work, the switch may be defective. Check that all connections are tight. Check the switch, remove it from the circuit and test for failure with a continuity tester or multimeter set on the Ohms setting.
At the beginning of the circuit the hot source is connected to the common terminal on SW1. The neutral is spliced to the white cable wire and then spliced to the neutral terminal at L1, along with the white 2-cable wire running to L2 where it connects to the neutral terminal.
The traveler wires are run using the other 2-wire cable between the lights and continue on to the traveler terminals on SW2. They don’t connect to the fixtures at all.
Here the source is at SW1 and the light fixture comes immediately after. The source neutral is spliced through to the light fixture. At the light the travelers are splice together and run to the 4-way switch. At the 4-way, the hot wire from the common terminal on SW2 is splice through to the hot on the light fixture.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.