In this updated diagram 3-conductor cable runs between the receptacle and switch, and the red cable wire is used to carry the hot source to the bottom terminal on the switch. The neutral from the source is passed through to the switch box using the white wire and in this diagram the white wire is capped with a wire nut.
In this circuit a split receptacle is controlled by two separate switches. With this arrangement two lamps can be plugged into the same receptacle and each can be controlled separately from two different locations.
When the electrical source originates at a light fixture and it’s controlled from a remote location, a switch loop is used. The circuit pictured here is wired with 2-conductor cable running from the light to the switch location. The white cable wire in this switch loop is wrapped with black tape and connected to the bottom terminal on SW1 and the hot source at the light. The black wire is connected to the top terminal on SW1 and the hot terminal on the light fixture. The neutral from the source is connected directly to the neutral terminal on the light.
Three-way switches allow for controlling a light fixture from two separate locations, these are usually used at the top and bottom of a flight of stairs or at two different entrances to a room. On this page are several wiring diagrams that can be used to map 3 way lighting circuits depending on the location of the source with relation to the lights.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.