Source 2 comes in at the combo device where the hot and neutral wires are connected to their corresponding terminals on the receptacle half of the device.
The common terminals will always be connected to a hot wire, either from the source or on the light fixture. These connections can be reversed if it’s more convenient, as long as one of the 3 way common terminals connects to the hot source and the other one connects to the hot on the load, these circuits will work properly.
In this updated diagram 3-wire cable runs between the receptacle and SW2 to allow for splicing the neutral source through to the second switch box. Here the white is not used for hot but instead the extra, red wire serves that purpose for the second switch.
This outlet is commonly used for a heavy load such as a large air conditioner. The outlet should be wired to a dedicated 20-amp/240-volt circuit breaker in the service panel using 12|2 awg cable.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.