In a kitchen where only one outlet box is available and both a switch for a garbage disposal and a gfci receptacle are needed, a a switch/gfci combo can be used as in the diagram at this link.
The 4 way comes right after the light fixture, but before the second 3 way switch, making it fall between the two 3 ways as needed. It could also be installed on the other side of the light and the effect would be the same.
In this circuit, two fixtures are shown but more can be added by duplicating the wiring arrangement between the lights for each one added. Here the source is at SW1 and 3-wire cable runs from there to L1. Two, 2-wire cables run between the fixtures, and 3-wire cable runs from the last one to SW2.
The common terminals will always be connected to a hot wire, either from the source or on the light fixture. These connections can be reversed if it’s more convenient, as long as one of the 3 way common terminals connects to the hot source and the other one connects to the hot on the load, these circuits will work properly.
site,please contact and we will take action immediately, we will either remove the pictures soon.Contact • Copyright • Privacy • Terms
Copyright © 2018 Hotelshostels.com. All Rights Reserved.